You can email us at email@example.com, or write to us at 8403 NW 68Th ST – Miami – FL 33166 – United States.
Yes, it can be used for both sucking as well as blowing.
No, the BLOWER’S performance is higher when used for pressure and lower when used for vacuum.
Yes, the blower was developed to be utilized in both 50Hz and 60Hz.
No, usually the performance is 20% lower if it is installed in 50Hz as opposed to 60Hz.
The primary difference between 50 Hz and 60 Hz is that the latest is 20% higher in frequency, which will cause the speed of the induction motor and generator to be higher when compared to 50Hz.
If you are interested in becoming a reseller or distributor, please email us at firstname.lastname@example.org and tell us your plans as well as where you like to represent us.
The warranty is one year from the purchase date for any manufacture defects as it is stated in the Owner’s manual on page 13.
You should clean at least once every month the noise absorbing foam used in mufflers and the motor as well as the blower itself. Filter must be replaced at least twice a year, and mufflers should be checked on a monthly basis. Lubrication Interval To lubricate the bearings, the roller contact bearings and the adjacent bearing housing should have the used grease removed and replaced with fresh grease. About 50 percent of the roller balls should be filled. No more than 65 percent of the adjacent bearing housing should be filled. Sealed bearings should be replaced within the listed conditions below with new bearings ***** See chart on page 10 of the Owner’s Manual***
Please see pages 2 through 6 of the Owner’s Manual.
It is not recommended as any dirt particle that gets inside the blower will damage the impeller, which will cause it to stop working and warranty loss.
Yes, you can install 2 or more BLOWERS in parallel to obtain bigger results so you can meet the needs of your project.
Yes, you can install the blower in different electric voltages according to the diagrams contained on the label inside the electric installation compartment. 50Hz Three-phase (220V ~ 415V) 60Hz Three-phase (230V ~ 480V)
You can install an additional silencer or in some cases an enclosure sound proof (acoustic box) according to your needs.
Please consult page 12 of the Owner’s Manual.
Please consult page 6, items 1-5 of the Owner’s Manual.
The environment should be the cleanest possible to avoid dirt going inside.
Yes, we can guide you and help find the best model to replace your old BLOWER.
The difference is that single stage only has one impeller, while double stage has two.
We will answer within 48 hours of the request’s receipt.
Yes, we ship nationally and internationally through different methods and shipping prices according to our clients necessities.
IP54 and IP55
IP 54 is a grading usually marked on the products that are to be used in extreme conditions (Outdoor).The IP rating of any product specifies how resistant the device is to foreign objects and moisture. IP stands for Ingress Protection, meaning its ability to stand in extreme weather conditions.
A Totally Enclosed, Fan-Cooled (TEFC) electric motor is a type of industrial motor with an enclosure that does not permit outside air to freely circulate through the interior of it.This means that the motor is dust tight, and has a moderate water seal as well.
The performance was measured under 20º c air temperature and 1,013 mbar pressure.The allowable tolerance of performance value is +- 10%. The sound level was measured at a distance of 1.5m with the fully open inlet and outlet ports.
The blowers can run in 20,000hours under normal operating conditions. NOT OVERLOAD OPERATION. (Ambient Condition: Temperature: -20°C~40°C, Relative Humidity: 80%)
The bearing must be replaced or filled with grease in accordance with the bearing replacement cycle. It is as follows: 1. Grease replacement term of normal load operation.
High temperature, high speed grease. Recommended NLGI Grade N3. Recommended Fat: UNIREX N3